SEPAMAT system separator
The INTEWA "SEPAMAT" system separators separate the drinking water system from the consumer system. They protect the drinking water from contamination due to the backflow of substances from the consumer side. A system separator is placed between the municipal drinking water pipe and one or more consumers, which must be separated according to category 5 of the current drinking water regulation DIN EN 1717.
The "free outlet" is already integrated in the DVGW-certified SEPAMAT. According to the European standard EN1717, only the so-called "free outlet AA and AB" is approved for the replenishment with drinking water in case of water shortage. The SEPAMAT thus meets the highest safety requirements worldwide.
|Typ||Max. volume l/h||Max. pressure bar||Note|
|SMT F20-SC||5.400||2,5 - 5,0||Pressure level adjustable|
|SMT F40-SC||7.800||2,5 - 6,5||Pressure level adjustable|
|2 x SMT F20-SC||10.800||2,5 - 5,0||redundant parallel operation|
|2 x SMT F40-SC||15.600||2,5 - 6,5||redundant parallel operation|
|3 x SMT F20-SC||16.200||2,5 - 5,0||redundant parallel operation|
|3 x SMT F40-SC||23.400||2,5 - 6,5||redundant parallel operation|
The INTEWA SEPAMAT Profi separation station includes an integrated receiver tank, a double-pump booster system with self-priming multistage horizontal centrifugal pump and alternating start-up, and the electronic control system - all mounted in a housing made of powder-coated sheet steel.